Running-in of a new or overhauled diesel engine must be run in for 60 hours before it is officially used, and the generator lessor
can be put into full load use. The generator rental is to improve the working half of the diesel engine to protect the moving parts and improve the operation of the diesel engine. Reliability and service life. The running-in should be based on the diesel engine's use and the way of dragging, to consider the specific running-in plan. In principle, as the running-in time increases, the speed and load of the diesel engine are gradually increased. The power is preferably 50% -80%, and the speed should not be greater than 80% of the rated speed. However, at the beginning of the running-in period, the running time should not be too long in the case of dry running or too small load. Pistons, piston rings, connecting rod bearings and cranks are properly short-termed in accordance with the above-mentioned running-in conditions.
Normal use of diesel After the generator rental
diesel engine is put into normal use, the generator rental should always pay attention to the indications of all instruments and observe the dynamics of the whole machine; check the cooling system and the transmission surface of each part of the lubricant frequently. In case of damage or leakage, the cause should be supplemented or checked immediately and eliminated.
During the operation, especially when the load is suddenly reduced, care should be taken to prevent the speed of the diesel engine from suddenly rising above the prescribed value due to the failure of the governor, and emergency measures should be taken promptly when such a situation occurs. http://hzbxx.cn/
Dongguan Kangliang Motor Co., Ltd. generator rental, generator rental price, used generator recycling, used generator rental, used generator rental price, Dongguan Kangliang Mechanical and Electrical Equipment Co., Ltd.