Popular keywords: generator rental, generator rental price, used generator recycling, used generator rental, used generator rental price, used generator rental
Contact: Mr. Zhang
Generator installation rental six major points to note:
First, the installation site should be well ventilated, the generator side should have sufficient air inlets, and the diesel engine side should have good air outlets. Air outlet area
It should be more than 1.5 times larger than the water tank area.
Second, the surroundings of the installation site should be kept clean, and items that can generate corrosive gases such as acid and alkali should be avoided in the vicinity. Have
Conditions should be equipped with fire extinguishing devices.
3. For indoor use, the smoke exhaust pipe must be led to the outdoor, the pipe diameter must be ≥ the diameter of the smoke pipe of the muffler, and the elbow of the connected pipe
Should not exceed 3 to ensure smooth smoke exhaust, and the pipe should be tilted down 5-10 degrees to avoid rainwater injection; if the exhaust pipe is installed vertically upward
, You must install a rain cover.
4. When concrete is used for the foundation, the level of generator rental must be measured with a spirit level during installation to make the unit fixed on a level foundation. Unit and base
There should be special anti-shock pads or foot bolts between the foundations.
5. The unit casing must have reliable protective grounding. For generators that need to be directly grounded at the neutral point, it must be carried out by professionals.
Neutral grounding and lightning protection device. It is strictly prohibited to use the grounding device of the mains to directly ground the neutral point.
6. The two-way switch for generator rental and utility power must be very reliable to prevent reverse power transmission. Wiring reliability of bi-directional switches requires local power supply
Department inspection and approval. http://hzbxx.cn/